Euroklimat propane chillers group for the production of French cheese
Great installation of two EKO.E/MT B/ST/HR 3483S and one EKO.E/MT B/ST/HR 1642S with R290 refrigerant fluid for a cheese production site in the center of France near Clermont-Ferrand. Here, there is the production of famous French cheeses as "Le bleu de Laqueuille", "La Fourme dâAmbert AOP", "Le Bleu dâAuvergne AOP" and many others.
Each unit is equipped with semi-hermetic reciprocating compressors inverter driven, Shell & Tube evaporator (for the units 3483S), brazed plates evaporator (for 1642S unit), microchannel heat exchangers at condenser side, EC fans, anti-vibration rubber mounts and a double pumps hydronic kit fully in stainless steel.
All units are also equipped with two types of heat recovery: one partial heat recovery and one total-modulating heat recovery for each refrigerant circuit. This solution allows to recover the condensing heat that would otherwise be lost.
The nominal cooling capacity of the units 3483S is 330 kW with temperatures inlet/outlet of the evaporator at 1/-3 Â°C and an air DB temperature of 35 Â°C. Instead, the nominal cooling capacity of the unit 1642S is 158 kW with temperatures inlet/outlet of the evaporator at -3/-7 Â°C and an air DB temperature of 35 Â°C.
Euroklimat chiller for a bakery process in Australia
We are proud to share with you this interesting installation of this RAK.W-B/ST/SP 210C6, a Water-to-Water chiller used both comfort cooling and food industry process.
In particular, this unit during the summer period has two objectives: cooling the production site and offices for human comfort and cool down a subcritical CO2 unit, which cooling capacity is applied at a blast freezer to cool freshly made cakes.
The chiller is equipped with six R410A scroll compressors (three compressors per circuit), two Shell & Tube condensers, one dual circuit brazed plates evaporator, anti-vibration rubber mounts and an electromechanical flow switch.
The nominal cooling capacity is 627 kW with temperatures inlet/outlet of the evaporator at 12/6 Â°C and 29/35 Â°C at the condenser.
Discover this Euroklimat solution: water - to - water chiller with low GWP refrigerant for industrial process
Interesting installation of this EKW-B/SP/VFD 702 S, Water-to-Water chiller with low GWP refrigerant R513A used in a plant of HyCO (Hydrogen and Carbon Monoxide or Syngas) production in the east of Spain. This unit replaced an existing obsolete unit with R407C refrigerant.
The chiller task is to cool down a closed water circuit used to reduce the dew point of a CO2 stream upstream of a driers bed system and rejects heat to the plant cooling water system.
Equipped with two reciprocating compressors inverter driven, two Shell & Tubes condensers, one dual circuit Shell & Tubes evaporator, anti-vibration spring mounts and electromechanical flow switch.
The application requires tight control of the outlet fluid temperature (5 Â°C with tolerance within +/- 1 Â°C) and high reliability, because the chiller operates continuously.